Check manual page of apc_symmetra_test
APC Symmetra UPS: self test
|Distribution: ||official part of Check_MK|
|Supported Agents: ||SNMP|
This check monitors two OIDs of APC Symmetra UPS devices: The result of the last self test
and the last date of the self test run. The check becomes critical if the test result is
"failed" and it has a warning or ciritical state if the date of the last self test is more
than the warning or critical level ago.
The inventory process checks if the device has a system description OIDs (.22.214.171.124.126.96.36.199.0)
and if the name of this OID is known to the test. If this is true the system is inventorized.