Check manual page of carel_uniflair_cooling
Carel Uniflair cooling devices
This check monitors parameters of datacenter cooling devices
using a SNMP interface made by CAREL, which is i.e. used in the
Uniflair series of ACs.
The check only monitors part of the data supported by the MIB
since the MIB does not give info about potential values in
The check queries and goes to CRIT for any of these values:
the global status (this should catch any error)
water loss (one of multiple water-related values),
emergency operation mode (this is triggered following a
failure, running at maximum performance)
The check also queries the air humidity level, but currently
does not allow setting a level on this.
This check generates no item.
The check first looks for a cooling device vendor (this
is where it needs to be extended to cover other Carel devices),
then for the SNMP management device, and then for the MIB region
for cooling devices.
If all of these are found, the inventory creates a single service.